IP Router, MDRC
Connects the KNX bus with the Ethernet network. The device uses the KNXnet/IP protocol for communication (Routing and Tunnelling). It can be used as a fast line and area coupler.
The full filter table for main groups 0-31 is supported.
KNX devices can be programmed via the LAN using ETS. For this and further clients 5 Tunneling Server are available.
The IP address can be fixed or can be received from a DHCP server. Power supply via 12..30 V DC or PoE.
The KNX Standard Communication (Multicast) can be switched off. In this case, up to 10 IPR/S 3.1.1 can communicate using unicast communication.
- Auxiliary Voltage: 12...30 V DC (+10 % / -15 %) or PoE (IEEE 802.3af class 1)
- Auxiliary voltage current consumption: Maximum 120 mA at 12 V
- Current Consumption KNX: <10mA
- LAN Connection: RJ45 socket for 10/100BaseT, IEEE 802.3 Networks, AutoSensing